1.8KV 3KV XLPE Insulated Laid Up Aluminum Power cable
|FOB Price:||US $0.1-1 / Meter|
|Min. Order:||1,000 Meters|
|Min. Order||FOB Price|
|1,000 Meters||US $0.1-1/ Meter|
|Production Capacity:||50, 000m/Day|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: YJLV-1.8/3KV
- Voltage: 1.8/3KV
- Insulation Material: XLPE
- Material Shape: Round Wire
- Certification: ISO, CCC, CE, RoHS, UL, VDE
- Brand: Ronda
- Application Standard: IEC60502, IEC60228
- Trademark: Ronda
- Specification: YJLV-1.8/3KV
- HS Code: 8544601200
- Application: Construction, Overhead, Underground, Industrial, Power Station
- Current: DC & AC
- Sheath Material: PVC
- Wire Core Material: Aluminum
- Model: YJLV-1.8/3KV
- Colour: Customized
- Core: Copper
- Transport Package: Export Package
- Origin: Shanghai China
1.8/3KV XLPE Insulated Laid Up Aluminum Power cable
This cable is used as power distribution and transmission line at rated voltage 1.8/3KV which can be fixed installed.
1.The long time working temperature of the conductor should not be higher than 90 ºC
2.When conductor is in short-circuit (max. 5s), the conductor temperature should not higher than 250ºC.
3.While installation the ambient temperature should not be lower than 0 ºC and the bending radius should not be less than 10 times of outer diameter of cable.
3.Model & Name
Available model upon request as below.
|Copper Core XLPE Insulated PVC Sheathed Electric Cable (Cu/XLPE/PVC)|
Aluminum Core XLPE Insulated PVC Sheathed Electric Cable (Al/XLPE/PVC)
|Copper Core XLPE Insulated Steep Tape Armoured PVC Sheathed Electric Cable (Cu/XLPE/PVC/STA/PVC)|
Aluminum Core XLPE Insulated Steep Tape Armoured PVC Sheathed Electric Cable (Al/XLPE/PVC/STA/PVC)
|Copper Core XLPE Insulated Steep Wire Armoured PVC Sheathed Electric Cable (Cu/XLPE/PVC/SWA/PVC)|
Aluminum Core XLPE Insulated Steep Wire Armoured PVC Sheathed Electric Cable (Al/XLPE/PVC/SWA/PVC)
Note: Low smoke Zore Halogen, Flame Retardant, copper screened type are also available upon request.
5.1 Bending Radius
Single Core Cable Permitted Bending Radius=20 (d+D)±5%
Multi Cores Cable Permitted Bending Radius=15 (d+D)±5%
D=Outer Diameter Of Cable (mm)
d=Outer Diameter Of Conductor (mm)
5.2 Installation Temperature
Preheat is required when temperature is lower than 0ºC
5.3 Installation Drop
Cable Installation is not limited by level drop.